Client: Concentrator Plant in WA, Australia
IntelliSense.io, in partnership with BASF, recently embarked on an Optimization as a Service (OaaS) partnership with a mineral concentrator plant in Western Australia (“the client”).
The aim of this and other OaaS partnerships is to provide the client with the guidance and solutions required to unlock new operational value by means of digital transformation.
This Case Study outlines and reports on the initial phases of this partnership with the WA-based client, and the results achieved thus far.
Digitalization Road mapping
During the first phases of the project, IntelliSense.io worked with the client to map out their physical processes and operational workflows, and to understand the KPIs defining the success of their operation. IntelliSense.io and BASF did an analysis of the client’s process flowsheets and visited their site to become familiar with the client’s concentrator plant. This includes crushed ore stockpiles, a grinding, flotation, thickener and filtration circuit, as well as a large tailings storage facility.
IntelliSense.io did data analytics on the client’s historical data to review potential root causes behind the pain points described by operating personnel. In working with the on-site metallurgists, it became clear that they had a particular challenge with sufficiently drying their concentrate product without impeding on overall throughput. The concentrate drying processes, made up of the concentrate thickener- and filtration sections, were their process bottleneck. IntelliSense.io and BASF advised the client that the optimization of their concentrate thickener circuit would be a suitable focus for phase one of the OaaS partnership.
In addition to identifying the thickeners as the first area of focus, IntelliSense.io and BASF worked with the client to start mapping out what digital transformation could look like for them – delivering a continuous improvement roadmap to improve the client’s operation. In line with continuous improvement best practice, this roadmap was to be reviewed at the end of each phase, before proceeding to the next phase.
Thickener Circuit Improvements
IntelliSense.io and BASF demonstrated that the client’s thickener circuit had clear room for improved performance, and that improvement on the thickener circuit would significantly impact their overall process performance.
In conversation with operating personnel, the following key pain points were identified around their thickener circuit:
A historical data analysis by IntelliSense.io and BASF confirmed the pain points mentioned above. The recommended solution involved two parts, which will now be discussed:
- The improved control and optimization of Thickener 1
- Recommendations to the client on sensors and base layer control
Thickener Optimization Scope
In order to help the client’s metallurgists and operators with their operational decision-making around the thickeners, IntelliSense.io’s Thickener Optimization Application was implemented on Thickener 1 (one of two parallel concentrate thickeners). Initially, the plan was to do real-time optimization on all the concentrate thickeners, but the instrumentation challenges (see the next section) meant that IntelliSense.io and BASF decided to proceed only with Thickener 1.
The implementation of the Thickener Optimization Application on Thickener 1 involved:
- Integration with the client data sources
The connection with the client’s Data Historian, so IntelliSense.io’s brains.app decision-making platform automatically ingest both historical and live data.
- Configuration of a Digital Process Model for the thickener circuit
This involved the training of a machine learning based “digital twin”, which predicts the thickener performance based on the feed quantities, -properties and control variable settings.
- Configuration of the Optimizer’s Value Driver
This is the setup of Optimizer objectives and constraints, which is done with the client. This is to ensure that the Optimizer pursues “success” as defined by the client.
- Implementation and calibration of the Thickener Optimizer
The Digital Process Model is turned into an Optimizer, pursuing the objectives and adhering to the constraints set in the Value Driver. This Optimizer provides recommended setpoints for the available control variables, which are then implemented by control room Operators, or directly passed to lower level control systems.
Fig 1: Example of the Thickener Application’s Performance screen
The configured Value Driver consists of the following objectives simultaneously:
- Underflow % solids: maximise, but keep below an upper limit
- Flocculant dose: minimise flocculant usage
- Bed pressure: keep below an upper limit
- Rake torque: keep below an upper limit (protect rake)
- Mass balance: keep solids inventory in check
All control variables also had minimum, maximum and rate-of-change limits.
Fig 2: Ken Plozza from BASF monitoring the Thickener process via brains.app, configured in the client control room.
Thickener Optimization Results
IntelliSense.io and BASF implemented the Thickener Optimization Application, did on-site calibration, acceptance testing and Value Driver tuning with the client, trained the client on using the system and initiated the change management process.
In order to verify the process improvements brought about by the implementation of the Thickener Optimization Application on Thickener 1, IntelliSense.io and BASF did a thorough performance evaluation. This involved a sequence of ON-OFF testing with the client. During the ON periods, operators implemented the control variable setpoints recommended by the Thickener Optimization Application – and during the OFF periods they operated the thickener as they would otherwise. This testing was done over several days.
The results showed that the optimization of Thickener 1 done in phase 1 had significantly improved the thickener’s performance. When the operators followed the Thickener Optimization Application’s recommendations (“ON”), the thickener underflow density was stabilised against the upper limit provided by the client, whilst reducing flocculant usage by 16%, compared to the OFF periods. This can be seen clearly in Figure 1:
Fig 3: Example of the desired underflow %solids being achieved with much less flocculant. Flocculant variability due to adjustment to varying feed %solids and pH.
These improvements directly addressed the pain points raised by the client, and achieved what was targeted by the Value Driver. The client is now able to run their Thickener 1 filters at a much improved overall throughput, since:
- The thickener achieves a higher (but not too high) underflow % solids
- It runs at a much lower flocculant dose, decreasing the concentration of the filter- impacting flocculant in the underflow product
Additionally, the decreased flocculant dose means that the thickener overflow is made up of cleaner water, which greatly benefits the water treatment plant.
The lower flocculant doses meant that the thickener bed was less sticky and could proceed to the underflow more freely. This could be seen in the rake torque, which was 18% lower during the ON periods than the OFF periods, for the same rake height. It meant that operators did not have to do their characteristic “rake lifts” during the ON times, which led to more stable operation.
Sensor & Control Recommendations
A central part of IntelliSense.io and BASF’s Optimization-as-a-Service journey with a client is to review their process measurements, automated control and operational workflows. During phase 1 of this partnership, in parallel with the optimization of Thickener 1, IntelliSense.io did a review of the Data Quality and Control Quality on the client’s Thickener circuit.
These reviews revealed key areas for the client to bring improvements, which would add the most value to optimizing their thickener circuit. They were the following:
- Densitometer service/calibration
- IntelliSense.io’s Material Model showed that the mass balance does not hold over the flow meters and densitometers on the thickener circuit. The root cause was found to be the densitometer on the thickener feed – and IntelliSense.io and BASF advised the client that they would greatly benefit from doing a full service and recalibration of this instrument.
- Bed pressure installation/calibration
- Early data analyses showed that the bed pressure sensor on Thickener 2 was not covering the full operating spectrum, causing sensor clipping. The client was advised to adjust the sensor accordingly.
During the Control Quality assessment IntelliSense.io and BASF found that the level control loop on the thickener feed tank required tuning. It was found this control loop was a source of significant process variability in the overall process, and that improving the tuning of this PID controller would allow the thickener feed tank better to absorb fast upstream disturbances.
The first phase of the concentrator plant’s continuous improvement and optimization has delivered measurable value. Discussions are currently underway on capitalising on the instrumentation changes, by optimizing the thickener circuit as a whole. The overall process will then be analysed to review the client’s digital transformation roadmap. It is expected that the flotation circuit would provide significant room for improving the overall mineral recovery – especially as the feed material changes.
The initial phase of this OaaS partnership has demonstrated that it is possible to optimize the concentrate thickener circuit using an AI-based Optimization Application. The client’s target underflow density was achieved whilst reducing the flocculant usage by 16% – improving throughput through the value chain. The thickener rake torque was also reduced by an average of 18%, minimising equipment wear-and-tear.
Mine to Market: Value Chain Optimization
Powered and connected together by the brains.app platform, the Thickener Optimization Application is one of a suite of real-time decision-making applications that uses Artificial Intelligence (AI) to optimize each process; from mine-to-market.
Our Material flow model connects these applications together to drive even greater efficiency gains.